Will have hear again!
Gene even took his shoes off without being asked as he entered our home. Sine we do not wear our shoes in our home, we really appreciated his courtesy and respect. Of course he has corrected our concerns very quickly
Response from Folkes Heating, Cooling and Burner Service:
We are so happy to have been of service!
Checked operation of system. Found no refrigerant. R22 system. Recommended replacement due to obsolete refrigerant and age. Customer is receiving replacement estimate.
Installed line hide fitting for to complete install performed on 7/23/20.
Need senior tech to come back
Found fan center relay wired incorrectly. Also contactor relay electrically shorted. Replaced contactor and tested system operation. Need to bill for repairs.
Found breaker to furnace tripped, tested all components looked for an issue did not see one with the furnace or the cooling equipment. Customer needs an electrician as I think during remodeling they may have hit or clipped a wire.
Clean and service Oil with MA
Completed installation of external expansion tank. Filled and purged boiler. Ran system through several cycles. Pressure not exceeding 20psi and no leaking from relief valve.
Found pressure reaching 30psi when boiler is running. Relief valve opening. When boiler is off pressure reduces to 20psi. Need to get pricing and availability to replace OEM expansion tank.
Found water heater burner off on primary control. Reset burner running rough. Replaced oil filter, strainer and nozzle. Brushed heat exchanger and took combustion and efficiency test.
Installed new control board. Break tripped and transformer burnt out. Installed new transformer with low voltage fuse. Unplugged each component one by one and blew fuses each time. Short somewhere in boiler wiring or component. Need to look into replacing boiler. Customer would like estimate to replace.
Ran new gas line threw concrete from regulator to boiler. Removed existing gas line. Looped supply and return on boiler and filled boiler with antifreeze. Boiler pressure 15 psi.
Looked at boiler in garage. Water has been disconnected from boiler. No water in system. Need to drill through building to run gas line to new regulator. Would also need to pipe supply and return together to create a loop. Walter wants system filled with antifreeze to run and test system. Has not ran in 10 years.
Found new install Mitsubishi condenser a little under charged. Spoke with Kurt added 410a super heat 10degrees. Temps checked and all units cooling properly. Customer has another ac system for the downstairs of his house a carrier unit. Customer educated about pur air filtration and up ligh. Customer interested.
Replaced relief valve, Expansion tank (Extrol 60), & Air Vent on boiler, also added 10 gallons of anti-freeze, tested all zones, purged Second Floor water line ( air in lines), system operational all zones, also found 1st Floor ac not working, found tripped breaker, reset, tested, operational.
Bad expansion tank and air vent caused relief valve to open, and dump water, boiler is turned off and water lines are shut off until repairs are made, need to schedule appointment for Thursday to replace parts on boiler. ( customer requests Thursday appointment) And that includes expansion tank, air vent and relief valve.