Very professional, friendly service. Cost of service/diagnosis visit was reasonable. Only issue was the price for the fix we needed. One inclusive price for service - cost of part was next to nothing but labor cost was $$$$$.
Folkes does an excellent job diagnosing and fixing the problems. We had Danny out to repair one locations AC last week and Noah repaired another location today. Both did great work!
cost and installation pricing seems too high for amount of work and parts actually cost, otherwise I am satisfied by the job
She was very helpful and kept me updated about you technician.
Fan spinning very slowly and compressor not coming on. Found dead and leaking capacitor. Replaced capacitor and tested system everything came on. Also tested pressures while at unit and which were normal.
Found system pressures initially running at 70/245psi, superheat 42, sub cooling 0. System low on refrigerant. Performed electronic leak search. Found refrigerant leak on evaporator coil. Also found restriction in filter drier in condenser. Need to get pricing and availability on replacing coil and filter drier.
Replaced oem control board
On condenser air blowing not out of top of unit but blowing from the sides. Fan spinning in right direction capacitor and all wiring is wired how it should be. The first floor condenser short cycling system may have a possible leak will have to return tomorrow to pressure test system with nitrogen.
Found a burnt out control board, do not have a replacement ad looked to see if the universal board would work. We will need to give customer pricing and time frame if when we can get the board ordered and in the system.
Found system with no refrigerant. Leak searched entire system. Found leak at flare fitting for indoor unit. Tightened fitting,evacuated and recharged system. Checked operation.
Found emergency pan with water causing pan water sensor to trip and shutting power to communicating thermostat. Found condensate trough dripping water and blower pulling water past primary drain pan. Tightened screws on trough, which were never tightened down properly and leak stop. Had to replace pan sensor as it would not reset. Ran system through cycle and checked for leaks. Recommended annual maintenance.
Found power off to second floor system in attic. Turned back on and checked system operation. Second floor system running normally at this time. Turned on first floor system. Found system with no refrigerant. 18 year old R22 system. R22 is obsolete. And also R22 coils as well. First floor system needs replacement. Need to set appointment for replacement estimate.
Found faulty breaker in outdoor disconnect. Replaced with 60amp non-fused disconnect. Checked system running pressures and temperatures. Also tested capacitor microfarads and inspected contactor relay. Found capacitor microfarads low. Recommended replacement. Current running pressures 72/292psi, subcooling 17, superheat 2. Recommended replacement of capacitor.
Completed annual ac tune up on one system. Customer replaced filter upon arrival. Took temperatures and pressures. Cleared condensate line. Cleaned both coils.
Performed ac tune. Checked delta Ts, blower wheel, evaporator coil, cleared trap and drain. Checked pressures, checked capacitors and contactor. Installed Uv light. Customer put deposit of half with office, customer gave check for $321.61 for final payment. System is operating normally.
Found one thermostat bad on the first zone, the zoning panel was turning the condenser on and off intermittently, customer will need to replace the thermostat and zoning panel. Customer will try to replace himself he said, does not what it replaced now.
Found water in secondary drain pan. System off on water sensor. Poured water into primary pan and pan began overflowing immediately. Cleared drain line restriction with positive and negative pressure and water started draining. Poured high concentrate coil cleaner down drain and rechecked with several gallons of water.
Customer has a rodent problem keeps chewing and disconnecting wires at condenser. Fixed wiring and tested system. System running and operational
Estimate to replace heating and A/C. Approx 16 years old. Customer. Elvis and maybe Victoria will be present.