Will be in touch with estimate to install radiant in back room above pool and install a zone panel for boiler.
Thermostat had p9 code, customer cleared water out of secondary pan, found a cracked drain trap, replaced the trap and tested, reset the wireless thermostat and system is operating normally.
Clean and service Oil, recommend residential replacement. Boiler has a high amount of calcium build up inside cast iron, making loud noise, pressure keeps exceeding over 30 causing relief valve to open, system also has bad expansion tank.
Need to install mixing valve to take car3 of problem
Breaker tripped for heat pump. Found melted wire at hermetic terminal on capacitor. Re made wire connection. Compressor ran for 30 seconds. Internal valves sound broken and tripped breaker. Will not reset or run. Heat pump system needs to be replaced. Need to schedule estimate for replacement.