Great but it was a man
Excellent could not be better
Arrived to customers house and was informed we have been here before and that we just need to finish the last 5 vents and the return and supply trunk. Cleaned out the last 5 vents which were dirty along with the return trunk and supply trunk. The return trunk we entered at two spots as it was very dirty and the supply was also cleaned.
Customer stated only air handler working, went to condenser which was not running opened unit and found contactor very badly burnt but had no power coming to unit, found breaker tripped for compressor, reset breaker and unit came on, tested pressures which were very low system is from 2004 and does have R22. Customer did not want to do any repairs at this time. Turned system off at thermostat.
Relocate condenser to other side of the house by the main entrance behind the steps electrician came relocated disconnect bo all so brazed in ,pressure test and evacuate system did a start up customer was please whit everything
Price includes no financing
Arrived and found burner tripped. Reset and burner would not light. Checked for oil and spark. Pulled the nozzle assembly which the head was covered is soot and very dirty. Customer has a scheduled appointment with another company in a few days for a cleaning. Cleaned the head and electrodes, changed the nozzle and tested the system. No other issues to report. Boiler is not Sooted.
System low on refrigerant again customer didnâ€™t want to recharge system she sold the house.
Found condenser not energizing. Found only 120v coming into condenser. Checked outdoor disconnect, found no damaged wires or lugs. Found faulty breaker. Customer needs electrician to replace. Customer is selling home.
Found evaporator coil, line set and compressor frozen. Shut system down to thaw. Blower is running and filter is new. Need to return to finish diagnostic once system is thawed.
Performed ac tune up on system. System is 21 years old. Condensate pump was not working properly, recommended to replace. Capacitor on blower was very low, delta t was at 16, hooked up gauges to condenser and system would not give me a pressure reading. System is blowing cold air and operating. Customer does not have the money and does not wish to repair parts. Highly recommended a residential replacement. System is currently operating.
No oil leak, recommend residential replacement.
Arrived at customer home for acid cleaning explained to customer that a water heater is a better option than flushing coil. Customer decided to go with a 50 gallon electric water heater. He is going to have his electrician run a line for it and will call once line in ready. Flushed hot water coil For customer to get hot water running until hot water heater is installed
Hot water coil corroded over with calcium build up, causing no pressure at hot water lines and no hot water.
Clean and service Gas with MA, recommend residential replacement.
Arrived at home for customer complaint of toilet constantly running. Found fill valve stuck running water going into overflow. Replaced fill valve checked and tested.
AC tune up