Great but it was a man
Excellent could not be better
Performed ac tune up on system. System is 21 years old. Condensate pump was not working properly, recommended to replace. Capacitor on blower was very low, delta t was at 16, hooked up gauges to condenser and system would not give me a pressure reading. System is blowing cold air and operating. Customer does not have the money and does not wish to repair parts. Highly recommended a residential replacement. System is currently operating.
No oil leak, recommend residential replacement.
Arrived at customer home for acid cleaning explained to customer that a water heater is a better option than flushing coil. Customer decided to go with a 50 gallon electric water heater. He is going to have his electrician run a line for it and will call once line in ready. Flushed hot water coil For customer to get hot water running until hot water heater is installed
Hot water coil corroded over with calcium build up, causing no pressure at hot water lines and no hot water.
Clean and service Gas with MA, recommend residential replacement.
Arrived at home for customer complaint of toilet constantly running. Found fill valve stuck running water going into overflow. Replaced fill valve checked and tested.
AC tune up
No A.c. batteries in thermostat