Very good no complaints
Chris was very Knowledgeable and respectful. We felt very comfortable and he walked us through the whole process.
I should have used Folkes from the beginning. Very honest, professional, knowledgeable and friendly. They have been fixing someone else’s mistakes!
Good, man. Thank you for his help
Very professional Help us with our
Replaced faulty flow control valve. Refilled boiler, purged and bled radiators.
Found flow check bleeding through hot water to second floor heating zone when boiler making hot water through indirect. Need to replace flow,check and fittings. B&g SA-1. Also checked operation of bedroom ductless system. Checked drainage with water. Also recommended to run system at lower fan speed for better humidity removal. Need to return to completed work.
Found ductless heat pump low on refrigerant. System had to be charged last season also. Line set for upstairs system within wall. No access to leak search. Recharged system to proper operating pressures and temperatures. No guarantees on leaking system. Recommended replacement.
Performed ac tune up. The thermostat location is not centralized causing the thermostat to read the master bedroom temperature before the other rooms are being satisfied. The system is from 1998. No issues at this time but itâ€™s is older and anything can happen with it.
Installed first company air handler with heating coil and Amana condenser, new refrigeration pipes, condensate pump and 20x20 Honeywell media filter.
Found first floor system with no refrigerant. 18 year old R22 system needs replacement.
Completed annual maintenance on ac system. Found secondary drain pan cracked. Also no float switch. Recommended replacement of drain pan.
Installed 36k Mitsubishi multi zone heat pump condenser with 4 wall mounted indoor units. 2 6k, 1 9k and 1 15k btu. New line hide, line sets, drain lines and wiring. Installed wireless interfaces for each indoor unit. *need to return to start up/test once line voltage is completed* Lineset for the upstairs 9k unit was kinked in the wall we had to cut open sheetrock to repair. Also cut open Sheetrock to connect drain line. Mark from HPM is aware of this. Also need to repair piping at flo control valve on boiler. Need 1â€ pipe, 90s And 1â€ pex to sweat fitting.
Need to move, secure/adjust the pex lines in basement in some locations that the homeowner pointed out. A couple of spots where the line is going to need to be cut and routed differently.
Cleaned and serviced oil boiler.
Cleaned and serviced one oil boiler with first year install.
Condensate trap disconnected, reconnected cleared line and vacuumed up water in basement.
Systems operational, Bedroom unit low on r-22, charged, tested, Schedule appointment to install steam humidifier for bedrooms, paid in full, recommend residential replacement on both units.
Performed AC tune up for new customer. Changed return air filter, taped unit in a spot where air was getting out on return side. Tested capacitor and blower wheel amp readings all looked good. Did not have a good delta T reading was only about 5 degrees. Outside pressures were very low so we agreed to recharge system
Completed annual maintenance on ac system. Found original installer never wired hydro air handler proper for heating and cooling. Installed isolation relay, rewired low voltage controls and checked operation of heat and ac. Found broken emergency drain pan. Recommended replacement of secondary drain pan.