Very good no complaints
Chris was very Knowledgeable and respectful. We felt very comfortable and he walked us through the whole process.
I should have used Folkes from the beginning. Very honest, professional, knowledgeable and friendly. They have been fixing someone else’s mistakes!
Good, man. Thank you for his help
Very professional Help us with our
Condensate trap disconnected, reconnected cleared line and vacuumed up water in basement.
Systems operational, Bedroom unit low on r-22, charged, tested, Schedule appointment to install steam humidifier for bedrooms, paid in full, recommend residential replacement on both units.
Performed AC tune up for new customer. Changed return air filter, taped unit in a spot where air was getting out on return side. Tested capacitor and blower wheel amp readings all looked good. Did not have a good delta T reading was only about 5 degrees. Outside pressures were very low so we agreed to recharge system
Completed annual maintenance on ac system. Found original installer never wired hydro air handler proper for heating and cooling. Installed isolation relay, rewired low voltage controls and checked operation of heat and ac. Found broken emergency drain pan. Recommended replacement of secondary drain pan.
To much heat due to bad zone valve, replaced, tested, system operational,
Call back. Needs new hot Surface igniter, Customer to order part and install
No heat due to bad blower motor, needs to be replaced.
Found boiler relay in air handler stuck closed causing constant heat to hydro air handler. Replaced boiler relay. Tested operation in heating and cooling modes. Checked refrigerant pressures in both systems, o.k..
Checked over system operation. Running pressures and temperatures good. Filters, evaporator and blower wheel clean. Recommended enzyme filters to be replaced. Customer will get himself. Customer was not quoted diagnostic, was told this was a warranty call.
Ac tune x2
Leak on boiler