Dave Greer came the next day after I called the office to request help. He quickly discovered what the issue was and was able to fix it during this same visit.
Honest, trust-able, and reasonable, great company, great people
Checked a Trane heat pump with Honeywell thermostats on a 2-zone system. Found thermostats not properly set up use with heat pumps. Set up the thermostats.
Upstairs is a Trane heat pump from 2011, took amp draw on back up heat, tightened wires, tightened wires outside and. He led refrigerant levels they were good. The downstairs is a gas package unit made by Goodman from 2004. Checked safeties cleared pressure switch, tightened wires, cleaned flame rod.
Checked a Carrier gas furnace and replaced the furnace control board. Also replaced thermostat with Honeywell T-4.
Completed spring Tune-ups to 3 Goodman A/c units. Cleaned coils and cleared drain lines. Added 1.5-lbs Puron to downstairs A/C and 1.5-lb Puron to the 2nd floor A/C. Adjusted charge for 3rd floor A/C.
Checked a Trane HP system. Reset the GFCI outside that controls the condensate pump. Pun is working fine. Re-ran drain line and installed a coupling and barb fitting (minor drain repair). Puron was good.
Conducted spring tune-up. Cleaned condenser coils, cleared drain lines, and checked refrigerant. All ok. The filters are in need of changing in the next week or so.
Conducted spring tune-up on 2 Lennox A/C’s. Cleaned condenser coils and added 1-lb Freon to the downstairs unit.
Replaced a Honeywell 3-zone board and tested all zones - on and off. Everything performed perfectly.
Found a drain line on a evaporator coil was open allowing water to get into the house. Fixed drain issue.