I would highly recommend Greer for any HVAC projects, regular service, problems or install. They are the most honest and reliable service I have found and have used them for the past 6 years.
David was efficient and knowledgeable.
Thanks for keeping us up and running!!
None of the big service names had any interest in repairing my older equipment, they just pushed expensive new replacements. I wasn't ready to upgrade, and fortunately my neighbor recommended that I call Greer. They kept my aging units going until there was more rust than metal, and finally I gave in and had them put in fancy new units at a fair price. I am very happy with the result and as claimed, they work better and use less electricity. Today my installation team came back out for our spring tune-up and it was like a reunion of old friends. I genuinely like these guys and if you enjoy doing business with competent, honest local folks who care, you will too.
Very proffesional, great job
Installation of a new Gas Pack
Added 3-lbs Puron refrigerant to a Lennox gas pack.
Replaced a bad capacitor in a Carrier air conditioner. Cleaned condenser coil.
Checked Rheem heat pump. Replaced contactor. Checked Puron.
Provided a quote for replacement of HVAC
Provided quote for HVAC
I serviced a Heat Pump for the third floor, and an Amana Gas Furnace. I checked the refrigerant in the heat pump, and it was in all good order. I checked the safeties, took amp draws, and tightened wiring.
Provided a Quote for outdoor unit and evaporator coil
Lennox furnace hot surface igniter needed service.
Cleaned Trane heat pump condensing unit. Cleared drain, tightened wires. Checked refrigerant was good.
Preformed maintenance on a Trane has package unit. Tightened wires, checked pressure switch and checked safeties. Cleaned flame rod. Got leaves out of unit and off hood.
Preformed maintenance on a 2010 Trane duel fuel Trane package unit. Tightened wires took amps, checked evaporator coil it was clean. Then checked the furnace side of it and cleared pressure switch, checked safeties, checked flame rod and hot surface igniter all working in manufacturers specifications.
Preformed maintenance on a Goodman straight AC. Cleaned outdoor coil, cleared drain, tightened wires, checked refrigerant everything was running like it’s supposed to.
Conducted 2 spring tune ups for a Rheem A/C and a Trane A/C system. Cleaned 2 condenser coils and added 1.5 lbs Puron (R-410a) refrigerant to each and cleared the drain lines.
Preformed 2 maintenance’s on 4 year old Carrier units one is a heat pump and the other is a straight AC. Cleaned both coils and cleared drains and tightened wires and checked refrigerant everything was running like it’s supposed to.