I have recently switched to Greer Service from another company and have been very pleased with their maintenance service for my electric heat pump and air handler. David was very thorough in inspecting both the heat pump and the air handler.
Greer's is a great company with a deep bench of professionals that know HVAC systems inside and out. They always come through to keep my equipment running smoothly. Their service and warranty cannot be beat.
The crew came out three times in the past two weeks at short notice to fix my aging system. They correctly diagnosed and fixed a new problem with each visit, explained what was happening, and helped me prepare for what happens when I need a new system (mine is already a year past its expected life span). There was no additional charge for any of the visits. All was covered in my monthly plan. These guys are trustworthy, experienced, and effective.
Response from Greer's Service Company Inc.:
Thank you so much for the kind words. I’m sorry this took multiple visits but sometimes mechanical things don’t always want to cooperate. The good news is that you are back up and working well!
Cleaned outdoor coil tightened wires, cleared drain, checked refrigerant in normal operations
Preformed maintenance on a 2016 Trane heat pump. Tightened wires, took amp draws on back up heat, checked refrigerant all good system did go into defrost all ducts are sealed. System is running in manufacturers specifications.
Preformed maintenance on a 2010 Goodman 96% gas furnace. Checked safeties and pressure switches tightened wires took amp draw on system. Checked flame rod and igniter, cleared drain on the furnace side of it it is running in manufacturers specifications.
Preformed maintenance on 2 gas furnaces. Cleared drain, tightened wires, checked safeties and pressure switches. Both preforming in manufacturers specifications.
Preformed Maintenance on a 2011 Amana gas package unit. Tightened wires, checked safeties, checked pressure switch, it is running in manufacturers specifications.
Replaced duel capacitor. Took amps. Checked condensation pump
Checked A/C. Found drain clogged. Float switch had unit off. Cleared drain and checked system. All is ok.
Preformed real estate HVAC inspection on 2 gas packs.
Installed heat pump split system. Installed new duct work, new thermostat, and new zone board
Added 3 pounds of refrigerant as per real estate agents request.
Worked on a A/C system found it low on refrigerant. Recommended he call his warranty company before proceeding.
Replace dual capacitor on bigger unit. Took amps to make sure the motor was okay
Replaced the dual capacitor on the bigger A/C unit
Changed flame sensor and igniter electrode. Fixed heat
Changed flame sensor and ignitor electrode