Spring/summer tune-up for a Trane Heat Pump.
Preformed maintenance on a Lennox has furnace. Checked safeties cleared pressure switch was partially clogged. Tightened wires checked zone board and made sure wires were tight and the system was running in manufacturers specifications.
Installed a new furnace, condensing unit, and new duct work