Arrived and found no issues with system.checked heat rise and pressure. Subcooling is good. Need to order filter. 24x24x4 filter.
Performed annual maintenance on furnace.
Swept open firebox flue - has old vent pipe stabbed into flue but is not used and not connected to another appliance crown is cracked and needs repaired
Arrived to find unit in off position. Initiated call for cooling and system came directly on as requested. Applied gauges to condenser pressure was 125/325 advised customer that maintenance was required and was declined.
Fan setting is on causing continuous fan operation, explained system operation. Wants co detection installed sheâ€™s talking to husband about when
Unit had failed capacitor.
Performed annual maintenance on air conditioner.
Arrived and found t-stat not attached to wall very well. This was causing intermittent operation. Also found leaking schrader core. Replaced schrader core under P&L warranty. Charged system with 1lb of 410a. System is operating properly at this time. System would benefit from maintenance.