Arrived to find Lennox heat pump with disconnect out. Applied power and unit started to come on and fan slowly quit and compressor stopped, condenser unit in very poor condition Ed is giving bid while I was on site. EST to replace condenser motor and caps approximately 800$. Customer declined repair
Leaking water was due to very dirty filters causing excessive condensation on duct work. Changed filters and preformed cooling check, everything looks good.