Re-calibrated unit and ran diagnostics. Work performed by Christopher D.
Labor Warranty Check Performed by Travis W.
Arrived and found gasket was bad and not sealing. Replaced customer supplied gasket. Instructed to leave freezer shut for approx 4hrs.
Performed annual maintenance on equipment.
Arrived and found breaker tripped on what seems to be and hornets nest built against igniter. I removed nest and breaker turned on. System fired off and is operating properly at this time. Need to return with AA213 filter.
Not home no answer on phone 10-8-19 @10:43
Remove old equipment and haul away. Install new furnace, ac and coil. New disconnect and line set. New filter rack and return boot. Modify gas, electric, drains and flues. Ed Isaly 304.834.7444 Cell
Install new propane furnace, heat pump and coil (dual fuel). Remove old wood burner and ac. New pad, disconnect and line set. New filter rack and thermostat. New return drop and balance box. New pvc flue piping. Modify propane, electric and drain transitions as needed. Ed Isaly 304.834.7444 Cell