Don was one of the nicest sales people we have met in a long time! Made us feel very comfortable and made sure we understood everything! Was very patient and came out on a Sunday to take care of us!
The young man was very professional
Great, professional service today
Response from Grogg's Heating & Air Conditioning, Inc. (Parkersburg):
Thank you so much for your amazing feedback Gary and confidence in our services. Be sure to keep in mind all of our services. Please don't keep us a secret
Technician Greg has taken the time to look for, explain and address the issues. Appreciate the efforts put forth and the timeliness of Groggs repair services.
Service Call After Hours Fee 12+-year-old Nordyne system freezing, removed dirty filter, pressures were 95/250, added 2lbs of R410A pressures 135/305 system operating normally, advised the customer that system does have a leak and to begin looking into replacing system soon.
INSTALLED WARRANTY EVAPORATOR COIL
Diagnosed mini split leak, performed repair and added refrigerant.
Performed maintenance check on furnace
Yearly Maintenance Check Performed by Corey B.
Performed platinum check on package unit. Adjusted gas pressures down from 3.97 to 3.44. Cleaned condenser coil and checked amp draws and electrical. System is operating properly at this time.
Remove , replace wooden deck with new deck, and reconnect
20â€™ Lineset , pad to fit the AC , pull the power from the box to the AC