Travis was very courteous and did a good job.
Response from Grogg's Heating & Air Conditioning, Inc. (Parkersburg):
Thank you for the great review.
Capacitor on blower motor was weak preventing the blower from kicking on causing the system to trip on high limit. Replaced and system is now operating.
Older luxaire furnace had tripped blower cabinet limit downflow application. Possible causes power outage during call for heat or blower control board timer failure. Reset limit observed proper furnace operation cycled multiple complete cycles for heat with no malfunction cleaned flame sensor and checked motor amperage send receipt in mail please...
Unit was low on refrigerant. Added 2lbs of R410a refrigerant. Added leak seal.
Checked ac system all checks good, no filter in unit returning today for duct cleaning
Arrived and found t-stat improperly installed. Installed t-stat and turned stat to cool. Immediately found that switch to furnace was off. Flipped switch on and system is operating properly at this time. Blower wheel is a bit off balance and has build up. Also found piece of cardboard in wheel causing it to wobble. Due to age and condition of furnace it may be time to think about a more efficient system.
Unit had a failed capacitor, replaced and is running properly.
Performed annual maintenance on furnace and air conditioners.