Frederick was great, he was quick and efficient, courteous and took the time to explain everything he did for us. I am very pleased.
Response from Grogg's Home Services:
Thank you for the great review on Fred and your confidence in our services. Please consider us for all your Home Services needs. Don't keep us a secret.
Corrected the issue, system is performing great, and explained any questions about thermostat operation. Technician Christopher Dehnart
Commercial Service Fee Error code for open pressure switch. Resolved by removing two birds and a nest from the exhaust and inducer assembly. Condensate pump is cracked and should be replaced and the TXV needs Re-insulated. Customers gas provider is being contacted about the gas pressure dropping out, but after that is corrected, both systems should have a maintenance done to set the correct gas pressures. The inside of the heat exchanger is black with soot. This is a indication of a bad gas to oxygen ratio which is directly linking to gas pressure, if this is not adjusted in before use each year it will have a big impact on the life of the system as that build up of residue is acidic and will eat through the heat exchanger. Technician Christopher Dehnart Please include your tax exempt number when you call or mail in payment.
Performed Platinum Comfort Club Membership Tune-Up on Heating System 2021 Ruud heat pump system w/ AA213 filter. Replaced filter. Backup heat is propane. All checks good at this time
Service Call Platinum Client: Ductless unit in the IT room had a fault code for discharge temperature error. Checked the refrigerant pressure and found it to be low. Checked the flare fittings in the IT room for leaks and they were good. Found a leaking valve core on the suction valve outside at the condenser unit. Tightened valve and verified it was no longer leaking. Added 3 pounds of 410a refrigerant. Checked refrigerant pressure and temperatures. Everything checks out good. Delta T of 20 degrees inside the IT room. No further action needed at this time.
Service Call Fee: Upon inspection found unit very low on refrigerant customer stated they had another company put stop leak and a pound and a half of refrigerant beginning of week that has already leaked out. Suggested a new system.
Service Call Platinum Client- replaced failed capacitor on 17yr old ac unit. System has high head pressure (400psi). Unable to clean unit condenser coil today due the the water being shut off(water company is working on the water lines down the street). Set customer up on maintenance plan so the unit can be cleaned at a later date when maintenance is scheduled. Furnace is 27 yrs old and is showing it age. Blower motor is getting caked with dirt.
Examined system and found no issues. Filter size 20-25-1. Tested system in cooling and heat mode and was able to get both to work properly.
Performed Platinum Comfort Club Membership Tune-Up on Heating System. Performed maintenance on (4) 2009 Carrier Affinty split systems, and (1) mini split system with (1) head unit to cool server room. Note: systems use 55/6 capacitors for outdoor units, w/ 24x24x4 filters being used in a 5” wide filter casing if that size is more attainable. Systems are marked by number on filter slots, with system #4 having a flooded inducer caused by plugged drain. Cleared drain/trap/inducer. One system has a Honeywell direct intake steam humidifier. Adjusted Cozy plan from 1system to 5systems.
Service Call Fee: Adjusted Water Pressure Regulator and Put Proper Air Pressure in Thermal Expansion Tank.
THERM-X-TROL POTABLE WATER EXPANSION TANK