Hvac Installation Helper William Kraft
Line voltage polarity reversed from existing outlet, switched wiring at furnace switch, operating properly at this time, heat is working, customer will let us know Monday if they still need follow up call from install yesterday, initially furnace wouldnâ€™t fire, due to revereserd polarity, ok at this time.
Change 6 supplies from flex to hard pipe
Found compressor not pumping attempted hard start but was unable to break free set bid
Nut on liquid line entering evaporator was 1-2 turns loose. Tightened, charged unit, no additional leaks found at this time.
No voltage supplied to outdoor unit, breaker is melted, and bad wiring from main panel, need to have electrician repair breaker.
Unit iced up, need to follow up in am.
Please send invoice.