Response from Grogg's Heating & Air Conditioning, Inc. (Parkersburg):
Thank you for the great review.
Performed labor warranty check, ok at this time.
Performed maintenance check, cooling check was done in April, will renew next April, and schedule maintenance on new plan. Found blower capacitor failing, replaced, no additional issues at this time.
Service found coil frozen defrosted and checked for any leaks and found none replaced filter and pressure good system operating properly at this time.
Found transformer failed replaced and working properly at this time.
Unit condenser was dirty/blocked. Performed platinum maintenance check, cleaned coil, found capacitor failing. Replaced capacitor, system operating properly at this time.
Contactor failed, replaced, ok at this time.