Performed Platinum Comfort Club Membership Tune-Up on Cooling System: Performed yearly maintenance on the 22 year old air conditioner. Blower motor has buildup on it and temperatures coming out of the vents indicated a low refrigerant condition. Tried checking the pressures outside at the condenser and noticed the suction port has a decent leak coming from the shrader valve. Quoted blower cleaning and refrigerant charge. Quote is subject to change. Recommend looking into replacement at this time considering the age of the equipment and the outdated refrigerant type.