The Defend By Puronicss (Salted System)
Performed Platinum Comfort Club Membership Tune-Up on Heating System house was down to 67, set at 78. system running when I got here but hasnt ran in the last hour. no error code. went over system to find potential causes. found burners very dirty, found dip in flue pipe that is likely causing flooding/ pressure switch issue. this joint was also not glued. glued fitting and strapped up flue correcting the slope of the flue and preventing flooding from occuring in the future. checked gas pressures, changed filter, verified fan speed. system operating with 55 degree temperature rise. system is a 2003 Lennox 90% furnace. there is significant rust buildup and system is in poor condition due to lack of maintenance. recommend the customer prepare to replace it in the near future.
Replaced blower motor, furnace heating at this time.