Response from Grogg's Home Services:
Thank you for the great review and we hope you consider Grogg's in the future for all your Home Services needs.
Service Call Platinum Client Found port of inducer to be plugged with debris cleared obstruction and drained verified operation of furnace cycled furnace 3 times with 10 min run times no issues at this time .
Service Call Platinum Client: after replacing the flame sensor, furnace was having draft pressure issues. I removed the fresh air intake pipe from the top of the furnace and found several wasp nests. I removed the nests, blew out the vent with a shop vac, and furnace is now running with no issues
Performed Platinum Comfort Club Membership Tune-Up on Heating System: flame sensor is damaged in multiple areas. was able to run furnace but it does have flame sensing issues. gas pressure was a little high while 10IWC. I adjusted it down to 9.87. amp draw on the motors are both good. current filter was in incorrectly, replaced and showed customer the air flow arrow on the filter for future reference. ordered new flame sensor for trane furnace.
TXV leaking refrigerant. Tightening and added charge. Unit running good now.
Performed Platinum Comfort Club Membership Tune-Up on Cooling System: arrived to find system running rough with lots of condensation on the duct and a very dirty filter. outdoor coil on condensing unit was also very dirty. replaced the AA213 filter, cleaned outdoor coil, checked electrical components and adjusted airflow at the board to 1400cfm for 3.5ton ac. system is running well with good refrigerant pressures.
YORK-COLEMAN RUN CAPACITOR - S1-02420045700, 7.5 MFD, 370V
Description of work performed for Warranty Customer Changed out warranty gas valve and set gas pressures. Tested operation and performed maintenance on both systems. Customer has a run going to one side of the house that has a hole in the duct that is not accessible. Notified customer of issue.
Yearly Maintenance Check Performed by Travis W.
Electrical work including generator maintenance and whole home surge protector. Work performed by Russell Waggoner.
Service Call Platinum Client
Installed Tank-less Water Heater. Work Performed by Charlie H. & Matthew R.
Installed Tankless Water heater. Work performed by Charlie H. & Matthew R.
Arrived and found heat exchanger failed. Need to replace to make operable. Disabled furnace. Replaced filter for new system.