Corey did a great job servicing my HVAC system. I had several questions and he answered them right away, indicating his knowledge and experience.
So far I have been very satisfied with the service I received.
Service Call Platinum Client arrived to find condenser fan to be failed had 240v going to motor but no rotation. capacitor tested within range did replace fan motor and verified proper operation no issues at this time
#413 Replacement Media for Aprilaire 4400, 2410, & 3410
Performed Platinum Comfort Club Membership Tune-Up on Cooling System did preform cooling check on downstairs system capacitor tested at 44.7/5.02 of 45/5 is within tolerance standing pressures were 146 @ 46 ambient washed coil and condenser did brush electrical components did not find any issues
emergency service - no heat
Service Call Platinum Client diagnosed screeching coming from blower motor bearings. to quiet sound motor would need to replace motor. inspected system and found cracks at the top of the heat exchanger where it connects to the roof jack. system is unsafe to operate and needs to be replaced. customer would like an estimate to replace the system, comfort advisor Keith is present and providing estimate to replace. signed customer up on Cozy maintenance plan to waive service fee and give customer 5% discount on the new system.
Performed Platinum Comfort Club Membership Tune-Up on Heating System gas pressures set true temp rise 43 cleaned flame sensor all amp draws on motors show no issues system running good at this time didnadd surge protection to unit.
Performed heating and cooling preventative maintenance
PERFORMED HVAC SERVICE FOR CUSTOMER
PERFORMED HVAC MAINTENANCE
Performed HVAC Maintenance on furnace