Performed platinum maintenance check, need to order sensors for boiler.
Replaced circulator pump, hot water working properly at this time. Would like to have furnace maintenances scheduled before plan expires, 2 furnaces.
Circulator pump not working, has 120v, not pumping, hot water is only working briefly when call for heat. Have pics of pump, will order. Turned tstat for pump from 120 degrees to off until pump is replaced.