Response from Grogg's Heating & Air Conditioning, Inc. (Parkersburg):
Thank you for the great review.
Service Call Fee: the system had a very dirty condenser coil and very dirty filter cleaned both checked pressures and verified operations. cleanings are not covered under warranties.
Small gas leak at flex connection before furnace, tightened, checked all connections, ok at this time.
System was 1 1/2 lb low freon added dye to system operating properly at this time.