Filter was clogged replaced and system operating properly at this time.
Unit drain was clogged, cleared with c02, draining at this time.
Performed platinum maintenance check, furnace ok, ac was high pressure, cleaned coil, seems ok at this time, but wat leaking from drain pan. Recommend ac replacement due to age, and refrigerant.
Electrical Service- Set pole
Unit is operating properly, 21 degree temp split, good pressures. Thermostat was reading off 4 degrees from digital thermometer. Replaced stat, customer will allow system to run and call if unit does not cool properly.
Found both outdoor unit capacitors bad, and one blower fan capacitor bad, replaced all 3, units cooling air this time. Would like bid on installing mini split in board room on 3rd floor.
Electrical Service- Electrical Inspection