Service Call After Hours Fee Diagnosed cause of water in-floor is due to a clogged drain trap preventing condensation from draining out of the drain pan. Cleaned drain with a shop vac, cleaned and flushed with water and dish liquid. recommended yearly maintenance checks and flushing drain periodically to prevent future clogging
Set dip switches and added freon
Check system running fine
System needed jumper wire between y1 & y2 to kick into high fan speed system operating properly at this time.