Diagnosed issues with Trane spilt system. Reset power operation check per manufacturer specifications. Unit in proper working condition.
Installed new Honeywell TH5220D FocusPro 5000 thermostat.
Installed new heat sequencer
Performed complete inspection on system to make sure running properly. Unit in proper condition.
Installed new thermostat, condenser fan motor, and capacitor.
Installed new contactor.
Customer has a oil fired furnace and wants to change the system to a heat pump
Added 2 pounds of R-22 Refrigerant