Fast diagnosis, courteous, friendly. I would like Anthony to work on all my homes and rentals.
Replace capacitor for outdoor fan motor on air-conditioning system with upgraded heavy duty part longer part and labor warranty included
Follow up to replace indoor coil under manufacture part warranty. Recovered refrigerant from system. Removed and replaced indoor coil, biflow drier. Pressurized system to 300 PSI and checked for all connection made. Evacuated system down to 500 microns. Weight in 5lbs 13oz of fresh R410A. Cycled system on cooling and found system pressure 110/300 PSI. Supply air temp 50 and return 73 degrees. Cycled system on heating and found
blower motor, airflow, temp rise and system is all operating normally and within manufacture specifications at this time, ready for winter. Also performed whole house plumbing inspection, water heater in backyard has small amount of rust on hot water outlet, it is dry and ok now. 3 bathrooms, kitchen, laundry, water stops and supply hoses all ok. thank your for your continued confidence.
Perform service on a Rheem package heat pump system.
Perform service or both gas split systems.
Arrived in Gold canyon to perform a diagnostic service on a Lennox A/c with gas system. Rewired condensation pump. Tested condensate pump operation as well as condensate safety switch. Thank you very much for choosing Hobaica services. Have a wonderful day.
Presidential diagnostic for a landlord and tenant very old and inefficient air-conditioner need to be replaced soon
Residential preventative maintenance tune up AC, air handler and evaporator coil. Clean condenser coil and condensate drain line, check duct static pressure, airflow, refrigerant pressures, temperature split, air filter, compressor, motors and fans for best efficiency. Inspect air conditioner, capacitor, contactor, safeties, electrical, thank you for your continued confidence in our HVAC, wine cellar, and home performance energy audit services.
Ac check up
Ac check up
Performed a diagnostic in the air conditioning system.