I thought he did a fantastic job
Scott was our service technician assigned to do our “6 month check up” on the AC and furnace. He was very thorough and very courteous. Reassured us that all is well going into the hot summer here in Arizona. Went above and beyond to make sure all my questions and concerns were answered. He also changed out several of our smoke alarm batteries which was very much appreciated. Hobaica always calls to remind me when we are due for our 6 month check up. I also appreciate the communication that Hobaica provides regarding not only the name but also a picture of the technician that will be arriving. Thank you!
Fast diagnosis, courteous, friendly. I would like Anthony to work on all my homes and rentals.
HVAC System Maintenance Service. I arrived at the home to honor the $19.52 new customer coupon and perform a 16-point inspection on the client's HVAC system.
Thermostat replacement, please mention Sam & Grayson in your 5 stars google review
1952 new customer special, please mention Grayson in the google review
Tcc Silver Maintenance
Tcc bronze maintenance
Perform bi annual services.
Annual TCC Silver 1 Unit Bi-Annual Inspection (8-12)
Danny U. Performed seasonal maintenance on Sam and Karen’s Daiken heat pump. Here is the review link. A 5 star google review is the best type I can receive. You need a Gmail account though. Any 5 star review with my name being mentioned will make my day! Thank you for your time Sam. Semper Fi!
TCC SILVER 18 UNIT INSPECTION (8AM arrival time) ALSO $79.00 SERVICE CALL FOR ONE UNIT NOT HEATING ***THEY ARE DUE TO RENEW: QUOTED
Replace capacitor for outdoor fan motor on air-conditioning system with upgraded heavy duty part longer part and labor warranty included
Follow up to replace indoor coil under manufacture part warranty. Recovered refrigerant from system. Removed and replaced indoor coil, biflow drier. Pressurized system to 300 PSI and checked for all connection made. Evacuated system down to 500 microns. Weight in 5lbs 13oz of fresh R410A. Cycled system on cooling and found system pressure 110/300 PSI. Supply air temp 50 and return 73 degrees. Cycled system on heating and found
blower motor, airflow, temp rise and system is all operating normally and within manufacture specifications at this time, ready for winter. Also performed whole house plumbing inspection, water heater in backyard has small amount of rust on hot water outlet, it is dry and ok now. 3 bathrooms, kitchen, laundry, water stops and supply hoses all ok. thank your for your continued confidence.
Perform service on a Rheem package heat pump system.
Perform service or both gas split systems.
Arrived in Gold canyon to perform a diagnostic service on a Lennox A/c with gas system. Rewired condensation pump. Tested condensate pump operation as well as condensate safety switch. Thank you very much for choosing Hobaica services. Have a wonderful day.