Service Expert Tom Hayes is an excellent representative of Hobaica Services. Always comes to the home with a smile, is personable, and a friendly technician ready to go to work. His skills and knowledge of the job are top notch. He is careful when he enters the home with slippers and carries ladder and tool bag with care not to scratch or damage the walls etc.
A good experience.
Justin quickly diagnosed the problem with my AC unit, showed me the damaged area and priced the repair. He was able to complete the repair in time for me to participate in a work-related call, after I shared this concern. Very professional and courteous.
I emailed the office to inquire about a quote to fix my wine cellar a/c unit. They were very prompt in responding and not only scheduling a appointment but also searching for the best possible deal for me. They offered a first time client discount and managed to get a technician out to my house within the day of request. The technician was very professional. Upon arrival he put shoe covers over his feet to protect my home. Also he knew exactly what to do to fix our unit. He even went ahead and help find the best economical solution for the unit which was deciding between repair and replacement since the current unit is old. Overall great experience with both office staff and technician. Would highly recommend their services.
Angel and Issayas arrived on time. They were courteous and got right to work. The installation went smoothly. Angel went over the operation of all the new equipment and answered all my questions. They completely cleaned up the work area. A very professional team!
Justin was very knowledgeable and professional. He took his time and was very informative in explaining our various water heaters and ac equipment. He did an excellent job in the maintenance that was involved and I will always request him!
Air filters are extremely plugged up in the attic. (special trane size BAYFTAHEXM2) for both. (FilterFetch.com has them under code: c6ts-p3n) Possibly filters have not been changed for years. Return trip fee applies to return and change them out after customer orders filters. Both attic accesses from outside house. Thank you for your continued confidence.
Shut off valve repair
Performed diagnostic on a Trane communication system found the communicating wires had a break, once replaced with new wires we cycled in cooling calling for 1st and 2nd stage. As of now system is operating properly in cooling. Thank you for choosing hobaica
Plugged in and started up wine unit airhandler. Outside is powered on already. Found thermostat outside of wine room is unable connect to wireless sensor. Sensor batteries are dead, replaced with batteries from truck stock, used 2 aaa batteries. Batteries should be replaced every year. Started up wine system, Performed maintenance in cooling. Checked air filter, thermostat, coils, electrical, capacitors, controls, safeties, airflow, temperature split, refrigerant pressures, motors and bearings,
1994 split Lennox heat pump. Reversing valve selinoid is vibrating and was making a lot of noise until I adjusted Metal mounting bracket and tightened. now it is very quite. I did find system with #r22 has below manufacture level for pressures, high suoerheat and compressor could overheat. Estimated just replacing 13lbs factory charge with new environmentally friendly refrigerant could easily be over $1000. Replacing the system would be better idea. Went over tcc plans,
Perform bi null service for four gas split systems and a wine cellar refrigeration system.
Performed diagnostic on a no cool found low voltage wire chewed up, I respliced wires and reconnected after I tested unit and got approval for another repair. System is operating properly at this time.
Performed bi annual service for three carrier gas split systems.
Perform Hobaica special service for all four Amana gas split systems.
Arrived met with the owner continued to turn on thermostat engage cooling checked air handler filters and continued to inspect the split temperatures andCheck and clear condensate line after this I inspected the outdoor coil out door fan motor all electrical connections and over all condition I have found the inside air handler to be working to factory specs at this time but while checking the outdoor condenser a larger snake has made the underside its home from the inspection.
Met with Etty. She explained the unit does not turn on at all. Checked thermostat and found no voltage. Proceeded to the roof to inspect the unit. Found controls wires touching, blown control fuse. Reworded section of thermostat wire. Installed new fuse. Applied power. Called for cooling from the thermostat. Unit turned on in cooling. Inspected electrical mechanical
Completed maintenance on 3 systems.
Warranty first year, I carfully replaced the wine system start realy and capacitor. Per office we will return with overload. Compressor RST40C1-IAV-198Serial # 18H20731E Performed wine system maintenance. Checked coils, electrical, controls, safeties, airflow, temperature split, refrigerant pressures, motors and bearings, compressor and amperages, flushed condensate drain line and rinsed outdoor coil with water.
Perform bi annual service for all five HVACR systems.