Binn is very professional, efficient and explains in detail work needed when applicable.
Binh is great to have as my technician The job was over the top Looking forward to my 6 month review
Amer Khudher was well informed, polite and professional. You can send him to my house for every visit.
Brandon was professional and honest. I would recommend Hobaica to anyone who needs an honest company for their plumbing needs. I’m a first time customer, I will be back!
Amer was very professional and efficient.
Very courteous. Went out of his way to keep me informed.
New 4 ton package heat pump
3 - Y6604 and 2 - Y6605 filters. Condenser serial number 5817A01546, the TXV for indoor Coil serial 7116M11446 needs to be replaced With a new liquid line filter and all new refrigerant, 11 lbs r410a. System has had zero ice added previously however TXV is sticking closed. Performed maintenance in cooling on the rest of the systems, I Checked air filters, thermostats, coils, electrical, capacitors, controls, safeties, airflow, temperature split, Refrigerant pressures
Performed maintenance in cooling. Checked air filter, thermostat, coils, electrical, capacitors, controls, safeties, airflow, temperature split, refrigerant pressures, motors and bearings, compressor and amperages, flushed condensate drain line and rinsed outdoor coil with water. System is operating normally and readings are within manufacture specifications at this time. Thank you for your continued confidence.
Today customer was home to check the Y and condenser refrigeration and HVAC unit is not cooling properly and does have a warranty
Check the wine system refrigeration unit that is down, last week the technician adjusted the metering device to access the refrigerant pressures as well as the superheat and sub cool of the unit. Nothing they
Check for the new one sister not holding temperature properly.
Warranty Service Repair, tech to determine warranty (4-7) customer said she is having an issue with her second evap and we just did maintenance and now it is not working
Performed a biannual maintenance on 3 Lennox split heat pumps. Checked: Electrical connections Wiring Capacitors Amp draws Motors Bearings Contactors Start kits Temperature splits Static pressures Refrigerant pressures Superheat Subcool Reversing valve operation Relays Coil condition Drain pan condition Drain lines cleared with dry nitrogen Duct seal at units Fused disconnects I checked the units in cooling and found all components are operating properly and efficiently at this time.
49.00 Cooling Tune Up Special (12-4) *wine system*
Please sched startup of wine system Ductless wall mount CU on roof
79.00 HVAC Club Service Fee ***TECH TO COLLECT*** (12-4) HOUR LEAD TIME NEEDED TO MEET US, CALL GREG THE TNT / SD THE NEST T-STAT WILL NOT COMMUNICATE WITH THE SYSTEM
$69 X 2 Service Special Fee ***TECH TO COLLECT*** (8-12) MINI SPLITS