Very courteous and prompt
Jose and Jacob were on time, very professional, and finished in a timely manner. I just have one tip for future home visits. The humidifier pad was in need of replacement. Either let the homeowner know or have them come to look. After they left I found a fine powder on the kitchen floor. It probably fell on carpet walking upstairs. Not a big deal but I would have preferred to come look.
He was very friendly and very respectful, he kept me informed, very nice young man,
Arrived on time and seemed to be hard at work.
Charge AC to proper freon pressures, unclog condensate drain, replace filter and test for proper operation.
Performing furnace tune up and inspection for a long time customer.
Performed furnace tune up on 2017 Amana. PM check on electrical and ignition systems, safety controls, flame sensor, service and test of humidifier. Also checked Air Bear filter and dampers. Cleaned system.
Perform AC tune up on 2005 Goodman. PM check on electrical, freon pressures, filter, air flow and performance of system. Check dampers and turn off humidifier. Clean AC. Replaced AC capacitor and test for proper operation.
Diagnosis on an older Lennox system that doesn’t seem to be keeping up.
Installed a new Amana 16 seer system.
Serviced a 2008 Trane Air Conditioner and installed a Damper Zoning system
We installed a new 14 seer Amana system
Install a State Select water heater and test for proper operation.
Performing ac tune up on 4 year old York system.
Performing tune up and recharging Lennox unit.
Performing a tune up on a 1 year old amana air conditioner
Perform AC tune up on 2010 Lennox. PM check on electrical, freon pressures, filter, air flow and performance of system. Check dampers, vents and turn off humidifier. Clean AC.
I replaced a bad ECM Module on a Lennox Furnace. I also installed a ECM Protector.
Diagnosed a bad ECM Module on a Lennox Blower Motor