Performed AC tune up on 2003 Rheem. PM check on electrical, refrigerant pressures, filter, air flow and performance of system. Cleaned AC.
Performed a air conditioner check out on a Tempstar unit.
Air conditioner tune up on a Rheem.
Performed an air-conditioner service because the Carrier air-conditioner was not cooling. Found the system to be iced up. Thawed out the system and checked all components. Started the air conditioner and found it was short of Freon. Added R-22 Freon to the system to proper pressures and temperatures.
Air conditioner would not cool the house. It was extremely dirty. I performed a complete maintenance tune up on the system. Air conditioner also had a bad capacitor that would not allow the fan motor to run. Replaced the capacitor and checked freon levels. It was short of freon. Added enough R-22 to bring to proper pressures and temperatures.