Tech arrive before me and started right to work. Explained problems and fixed them. Very reasonable rate.
I was sold a thermostat and according to tech that installed it that it would program humidity like old thermosts. Did. Come to find out tech lies Billy replCed my blower and told me that thermostat could not do that. I'm very disappointed. U should have put n my thermostat just like the old one . Same features.
My technician was very friendly and knowledgeable about the issue I was facing with my AC unit. I would definitely recommend!
The service tech. was courteous and respectful.
Billy, the technician, was friendly and thorough in inspecting my cooling unit. Recommendations were made to help the performance of the unit but no sales pressure. That’s what I like about this company, they are about quality of work and not about making sales. The pricing is also very good compared to some of the competition that is directly in The Heights area. I have been using this company for the past three years, highly recommend them.
Mr Phan was both professional and through
Performed heating inspection, checked all electrical components and sensors, checked carbon monoxide and temperature, system is working properly.
Came to site and fixed the ceiling grill which felt off from the ceiling
Perform diagnostic for no heating service call, found a clog air filter, recommended duct cleaning.
Performed heating inspection and recommended duct system to be upgraded.
Performed heat inspection, checked carbon monoxide, checked filter and duct system. The furnace is appeared to be working properly.
Dustin inspected the systems drain lines for water problems
Performed diagnostic and found clogs inside primary drain line, cleaned clogs using shop vac, unit is now working properly.
Dustin replaced Lennox condenser fan motor on downstairs system.
Clean drain line and reset the unit.
Performed seasonal maintenance on a Lennox R410 system in cool mode to ensure proper operation for the summer heat. Was a pleasure meeting you today.
Dustin performed the annual ac inspection on 2 Amana systems
Performed AC inspection, checked from indoor to outdoor units, checked frozen pressure, checked ampere draw. Recommend to upgrade duct work, recommended to replace capacitor.
A/C Not Cooling