Dustin was very professional and thorough in the service and estimates provided for correcting issues found. The cost estimates were quite high though so may need to look elsewhere for more reasonable pricing.
Dylan quickly diagnosed the problem with the outdoor unit on our heat pump and had it cleaned and corrected all on the same visit. He is also very personable and happy to answer questions.
Dustin performed the annual heating inspection on three systems.
Performed repairs on a Lennox condenser to restore service in cool mode. Thank you for the opportunity.
Dustin serviced Trane XL20i ac system
Performed AC inspection, checked indoor to outdoor units, checked Freon pressure, ch amp coed amp draw from compressor and motor, rinse unit with water to remove debris.
Performed 3 system seasonal maintenance to ensure proper operation for the summer heat. Thank you kindly for allowing me to assist with your HVAC needs today. Was a pleasure meeting you!
Performed repairs on Rheem air handler which had a clogged main drain line. System is fully operational upon today’s repairs. Thank you kindly for allowing me the opportunity to assist
No cooling after hours call in new waverly.
4 System A/C Maintenance
Ac not cooling
UNIT FREEZING UP. HEAT INSPECTION