Performed seasonal maintenance on 2 Lennox Air Handlers in Heat mode to ensure proper operation for the winter season. It was a pleasure assisting your family today!
Performed seasonal maintenance on a Carrier unit in Heat Mode to ensure proper operation for the upcoming winter season. Was a pleasure meeting your family!
Performed seasonal maintenance on a Lennox Upflow unit in Heat Mode to ensure proper operation for the upcoming winter season! Was truly a pleasure meeting you today.
Dustin serviced customers AC system
Dustin performed annual AC inspection
Performed diagnostic and found bad transformer after power surge. Replaced transformer and turned ac
Completed heating inspection to ensure the system is working properly, efficiently, and safely.
UNITS SWEATING BEGINNING TO RUST
Checked in with valued client, located equipment and began spring inspection. After a detailed inspection I found that their new unit was working in A-1 condition. The ODC passed all amperage test and cap was found to be good. Sub cool was found to be with in proper range for both heat and cool mode. The Airhandler was found to he clean at both the coils and the blower wheel. UV Light was working as it should be as well as all safety switches. Drain lines were found clear and free of debris at this moment. The duct work and insulation looked to be in good standing at this moment. Work Done Spring Inspection Work Suggested Hard Start Kit
RETURNED TO REPLACE WARRANTY PATRIOT UV LIGHT.