Performed heating inspection and checked upstair and downstair furnaces. The furnaces are appeared to be working properly.
Performed heating inspection, checked all electrical components, duct system, flame sensors, checked carbon monoxide and temperature.
Performed heating inspection, checked all electrical components, flame sensor,gas leak, carbon monoxide.
Performed heating inspection, checked furnace, checked electrical components, checked for gas leak, checked carbon monoxide.
Performed heat inspection for upstair and downstair units
Performed seasonal maintenance on a Lennox 5 ton upflow system in Heat Mode to ensure proper operation for the winter season. Was a pleasure meeting your family.
AC not cooling
Performed Spring AC inspection, checked indoor to outdoor units, checked Freon pressure, checked ampere draw, checked drain line.
Performed annual cooling inspection
Performed AC inspection
Dylan preformed winter maintenance. Recommendations on drain and surge.
Dylan preformed commercial maintenance
Performing annual heat inspection