Non club heating maintenance. Joe(JC)Ritchal. 11/01/22 Performed full system evaluation and safety inspection. Checked blower motor, blower wheel, heat strips, safety’s, evaporator coil, reversing valve, compressor and fan motor amp draws, drain pan, float switch’s, drain line and changed filter that the customer provided. System is operating correctly at this time.