Blue club member maintenance. Joe (JC) Ritchal. 07/27/22. Performed full system evaluation and safety inspection. Condenser coil was extremely dirty. Pulled top off the condenser unit and washed out coil and cleaned out the bottom off the unit. Also changed three 1 inch pleated filters and the polarized media filters. Checked refrigerant charge and had subcool of 11. System calls for 13. Checked evaporator coil, blower wheel and motor, checked compressor and fan motor amp draws and checked capacitor. System is operating correctly at this time.