I arrived for a red membership ac pm. I inspect the system and found the evaporator coil to have been replaced. The new coil is install in the old coil box. The coil is to big for the coil box and the drain pan extends into the plenum. The plenum has been cut and the drain pan is sticking out of the front of the coil box and supply plenum. There is water overflowing into the secondary drain pan. Options to put a band-Aid on this is to put the horizontal system on a extended drain pan but this will only divert the water a different direction and not fix the coil issues. The coil would need to be replace in a coil box that it is made for for this to be corrected.