Tyler April 6. I arrived for blue shield ac service. Customer had just changed filter so left extra for him. Inspected blower compartment and evaporator coil. Went outside and checked refrigerant charge. Checked compressor and condenser fan amps. Checked electrical connections. Found dual run capacitor out of tolerance. Talked with customer and he wanted to replace it. Got it replaced. Removed top off condenser and removed leaves in bottom and washed coil inside out. Unit operating properly at this time.