Blue shield summer service x 2. Replaced filters. Blower motors are ECM, run capacitors not required, motors and wheels are clean, indoor coils are clean, condensate drain lines are clear. Condenser coils are clean. Both dual run capacitors tested bad on compressor side. Replaced both capacitors under 10yr part and labor warranty. Contactor points tested good. Checked operation, all amps and pressures are good. Both systems are operating normally.