09AUG2022 Jason B Arrived for possible recall no cool. Spoke with homeowner about the issue. Isaac was out and got it working, we already replaced the capacitor. However the AC won’t come on and won’t hum. Inspected AC found contactor failed. With homeowner permission I replaced the contactor. Verified amps to fan and compressor. Checked capacitors. Buttoned up system. System is cooling properly at this time. I am waiving the service fee as we were just out.