Unit frozen. Need to let thaw out. 7-11-2022– returned and removed top from unit and found indoor coil plugged and drain pan full of debris. Brushed coil and cleaned with rinse less coil cleaner, removed debris from drain pan. Checked operation. All amps and pressures are good. Have a 20 degrees air temperature drop. System is operating normally.