Ray F 8/16/22 Arrived to a blue club member ac tune up and the customer met me at the garage. I introduced myself and asked how his air conditioner has been working. He informed me that it has been working great. We inspected the system in the attic and found the evaporator coil to be clean. The blower motor, wheel and housing are also clean. Blower amps are normal and the run capacitor is within manufacturer specifications. Condensate drain line is clear. Wiring is in good condition. Return and supply of 73 and 53. Attic insulation is sufficient and ductwork in good condition. Inspected condenser and found he refrigerant levels normal. Contactor, wiring and disconnect are in good condition. Compressor and condenser fan motor amps are ok. Cleaned condenser coils. System is cooling properly at this time. Thank you for your business.