No cool/ blue shield summer service. Homeowner maintains own filters due to allergies. Found both sides of dual run capacitor to be bad, replaced dual run capacitor and checked operation, all amps and pressures are good. Required subcooling is 10 degrees +/- 3 degrees, actual subcooling was 10.2 degrees, superheat was 11.9 degrees. System is operating normally.