28JUL2022 Jason B Arrived for recent install no cool. Spoke with homeowners son about issue. Shirley got home and the equipment was not on/ would not come on. Inspected furnace found error for open secondary voltage. Checked wires found short on common. Inspected AC found wire jackets ripped and shorting to the frame of the AC. Stripped wires back and reconnected. Cycled system in cooling. Noticed wiggle in stat. Replaced Anchors and remounted stat. Checked temperature spilt 21 degrees delta T. System is cooling properly at this time.