Blue SPP ac maintenance. Asked about filters, hot and cold spots, condensate line, hot water tank and dryer vent from previous visits. Customer just changed filters at beginning of month. Customer mentioned the condensate line had a small drip, likely from condensation from cold water running out. Also mentioned new puppy had chewed on outside insulation on line set. Will replace 8â€ of armaflex insulation. Washed condenser thoroughly, inspect dual capacitor and fan side is still within range at 4.28 mfd, but will likely need to be replaced next year. Cycled system in and checked refrigerant pressure via delta t and amps. Checked outside surge protector. Went inside and checked blower and evap coil, amp draws and condensate line. Checked float switch and watched water flowing properly from evap coil into drain. Found a small piece of debris that was causing main condensate drain to possibly run higher than intended. Removed obstruction and verified proper water flow.
Dryer vent cleaning exhausting out roof.
2 System Bryant high efficient furnace winter heat tune up
Amana 95% high efficient furnace winter tune up.
Condensate leak on evaporator coil. Water dripping over edge of pan. Fix condensate leak. Cycled system and check for water leaks.
Repair a self installed minisplit. Redo flare fittings. Pressure check lineset, pull a vacuum and weigh in r410a refrigerant
Carrier AC summertime tune up. Wash ac coil and check charge
AC preventative maintenance for Carrier 14 SEER split system. Dryer vent cleaning through the roof.
Checked two Armstrong ac systems for summer
Give estimate to replace system
Furnace tune up
Replace induced draft pressure switch to carrier furnace
Preventative Maintenance Service on Carrier Furnace
Preventative Maintenance Service on Amana High Efficiency Furnace
Repair the air conditioner