I arrived for a new customer system replacement bid. I spoke with the homeowner and she wanted bids on a heatpump with a propane furnace. We bid a 16 seer and a 14 seer. The system will come with a new thermostat and a new condenser pad to set the condenser on. We will removed the old equipment and hall off all equipment. The new carriers system will have a 10year parts warranty and a 1 year labor warranty.
I arrived for a blue member fall tune up on a system we installed. I spoke with the homeowner and found only one issue with the flue for the furnace and water heater to be leaking water when it storms. I inspected the flue and sealed the roof jack. I then inspected the system and replaced all filters. I checked all electrical components gas pressures temperature rise and statistics pressures and found no issues with the system at this time. I recommended to flush the water heater and clean the burner compartment at this time. We decided to try and clean the water heat On the next service.
45 lights per bay each bay is 1666 sq ft 10 ton per bay there are 3 bays. I will get pricing on 1p ton package units.
I arrived for a fall maintenance for blue club membership on a air handler. I inspected the air ha and for the coil to be clean but the filter to be dirty. I replaced the filter and checked the system operation. I found all heat strips to be running between 21 and 23 amps. I found the blower motor to be running at 7.2 amps. I found the temp rise or be 23 deg with a max air temperature of 123 deg. I reassembled the air handler and checked the condenser and found it to be stopped up. I cleaned the condenser and suggested to add surge protectors to the system to help prevent repairs. Overall this system is running properly at this time.
Fall service tune ups on 2 heat pump and air handler systems. Upstairs system has not been working well. Inspected and found system not powering on at air handler, due to water filling back up drain float switch. With customer approval, cleaned back up drain and added drain pan treatment. Tested and found that contactor was also bad. Tried replacing with identical unit that customer had for spare parts, but that contactor had gone bad from a compressor burn out. Replaced contactor with a new one under parts warranty, but still need to charge for labor. Upstairs system now cooling properly, also cleaned out both heat pump condensers while repairing unit outside. Changed filters, customer supplied. Air handler tune ups. Tested drains, evaporator coils, blowers, blower capacitors, sequencers and heat strips. Tested reversing valves, and unit operation in heating, emergency heat and back to cooling modes. Tested amp draws, and voltage drop on compressors. Both systems working well for he
On September 2nd, 2021 I arrived to a blue shield customer for a 2 system tune up upon arrival I greeted the customer and then went to the thermostat to turn both units on i then went to the furnace in the closet and did amp drawl on the motor 3.1 amp and 47* air coming out of the system I then went to the condenser did amp draws on compressor 10 amps and fan was 2.1 amp checked charge had 13* subcooling I then went to package unit and did amp drawls on compressor 14 amp blower was pulling 4.5 amp washed condenser coils and everything is working properly at this time thank you for your business mike t
I arrived for a warranty call on a system we recently installed. I inspected the system and found the drain line to be full of water and this is what was causing the system to cycle on and off. I cut and installed a Jones valve on the system and blew it out with nitrogen and four all the water in the primary pan to empty. I then cycled the system back on and checked the drain line behind the water heater and found it to be draining water normally.
24AUG2021 Jason B Arrived at blue club not cooling well, spoke with staff about systems performance. This is the 2010 package unitChecked charge, amps, coil and capacitors. Everything is running to the best of its abilities. Thermostat is set at 65 degrees and outside ambient is at 97 today. System is only reaching 70 degrees. The return for this system is about 25ft down the hall away from the areas itâ€™s trying to cool. This can cause issues as itâ€™s not recycling the air properly. Replaced filter, opened up vents all the way. Reattached vents falling off wall. This system is running to the best of its abilities.
Silver club summer service x 2. Washed condenser coils, both dual run caps are good, both contactors are good, checked operation,all amps and pressures are good. Both blower motor run caps are good, both motor wand wheels are clean, both indoor coils are clean, both condensate drains are clear. Both systems are operating normally
No cool, found bad dual run cap. Replaced capacitor,compressor still not starting. Checked windings, all windings are open. Compressor is not overheated. Compressor is bad. R-22 system. Recommended to homeowner that system be upgraded.
Red shield summer service, replaced filter, blower motor capacitor is good, blower motor and wheel are clean, indoor coil is clean. Washed condenser coil, compressor capacitor is good, condenser fan motor capacitor is good, checked operation, system operating normally. Condensate drain line is clear.
On July 8, 2021 I arrive to a previous customer nonmember upon arrival I greeted the customer they stated that their unit wasnâ€™t cooling right so I went to the condenser after asking the customer to turn the unit on a check to charge at 0Â° superheat 0Â° sub cooling went to the evaporator coal found it was dirty pictures are attached I clean the evaporator coil check the charge again I had 10Â° sub cooling 11Â° superheat everything is working properly at this time thank you for your business Mike T
Came out to perform preventative maintenance on Mini Split system for customer. We have done work for him before on the same system, he just wanted it looked at and tuned up. I washed the condenser coil thoroughly. Customer already cleaned the filters inside. I checked compressor, fan motor, electrical components, temperatures and pressures of mini split. System is cooling properly within manufactured specifications at this time. Refrigerant was not needed.
Came out to call. Customer stated that the outside system wasnâ€™t coming on like it normally did and was making a different noise he got it to work for a little bit yesterday after having it off, but now itâ€™s not doing anything. I checked system over and found the capacitor depleted and the system not being able to run. Hard start kit got the compressor to turn over, but thatâ€™s it. I let customer know that the capacitor is bad and needs to be replaced. Capacitor is under part warranty, so customer only has to pay labor. I replaced the capacitor and went ahead and did the maintenance owed to the customer. Washed condenser coil thoroughly. Gave customer filters to change when needed. Inspected the contactor, compressor, fan motor, and condenser coil. Checked thermostat operation, amps, temperatures and pressures of condenser. System is now cooling properly within manufactured specifications at this time.
Silver club dual air handler and heat pump systems upstairs and downstairs in home. Spoke with customer about having hot water tank flushed today with tune up and they declined at this time. Asked how systems worked through recent snow storm and they did well. Customer mentioned they know filters are due to be changed and they will get fresh filters in tomorrow. Customer also mentioned they have had an ongoing issue of getting water in the downstairs ducts, and they just pump it out for the time being. Checked all capacitors, blowers sequencers and evaporator coils. Checked drain lines float switches and cabinet insulation quality. Both systems would do well to have pan treatments installed. Tested contactors and capacitors outside in heat pumps. Cycled systems on and checked electrical, refrigerant charge, reversing valves, defrost timers, and thermostat settings from heating to emergency heat modes. Fan motor on upstairs Armstrong air heat pump is reading higher than manufacturer