Ray F. 6/21/2022. Arrived to blue member ac tune up and customer greeted me at the front door. I introduced myself and asked how her system was working. She stated it is working great. I then asked where the thermostat, air filters and hvac equipment was located. She informed me and I proceeded to inspect the evaporator coil and furnace components. Evaporator coil is clean, as is the blower motor, wheel and housing. Blower motor is balanced. Amp draw and capacitor ok. Wiring in good condition. Condensate drain line is clear. Inspected condenser. Found refrigerant charge ok. Contactor and capacitor ok. Compressor and condenser fan motor amps are ok. Disconnect and wiring in good condition. Recommend adding surge protection to system. Cleaned condenser coils. System cooling properly at this time. Thank you for your business.