Red shield summer service. Replaced filter. Blower motor run capacitor tested good, motor and wheel are clean, indoor coil is clean, condensate drain line is clear. Condenser coil is clean, compressor and condenser fan motor capacitors tested good. No contactor. Control board is operating normally. Checked operation, all amps and pressures are good, subcooling is 8.9, superheat is 14.1 degrees, air temperature drop is 20 degrees, system is operating normally.