Ray F 8/18/22 Arrived to a silver club member ac tune up and the customer met me at the front door. I introduced myself and asked how her air conditioner has been working this season. She informed me that it has been working great and showed me where the equipment was located. I inspected the system in the garage closet and found the evaporator coil to be clean. The condensate drain line is clear. Blower motor, wheel and housing are clean. Blower amps are normal. Wiring is in good condition. Return and supply differential of 19 degrees. Inspected condenser and found the refrigerant levels normal. The contactor, wiring and disconnect are in good condition. Capacitor is within manufacturer specifications. Compressor and condenser fan motor amps are ok. Cleaned condenser coils. Recommend surge protection for the air conditioner and the furnace. System is cooling properly at this time. Thank you for your business.