Silver club summer service. Replaced filter. Blower motor is an ECM motor, run capacitor not required, motor and wheel are clean, indoor coil is clean, condensate drain line is clear. Washed condenser coil, compressor run capacitor tested good, condenser fan motor run capacitor tested good, contactor points are good, all electrical connections are tight. Checked operation, all amps and pressures are good. Required subcooling is 13 degrees +/- 3 degrees, actual subcooling was 10.8 degrees, superheat was 19 degrees, air temperature drop was 21 degrees. System is operating normally.