I arrived for a club member compressor replacement. I arrived and removed the old compressor and flushed the line set. I then installed the new compressor and pressure tested the system to 350 psi. I then pulled a vacuum down to 500 microns and added 6 pounds of R410A. I cycled the system on and found it to be running properly.